Note: I don’t have EzWare Plus software or the HMI and no specifics on software revisions or HMI hardware revisions or models. I have no sample project.
The following is based on what worked and was learned through support.
If a data field is declared as 32 bit in the Maple and you are trying to read an AKD parameter or AKD BASIC variable, the Maple needs an offset of 1 from the WB Help starting address and also word swapping.
For example in the AKD BASIC program